Questar Southern Trails Pipeline Company
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 06/01/2002, Docket: RP02-318-000, Status: Effective
Original Sheet No. 79 Original Sheet No. 79 : Effective
GENERAL TERMS AND CONDITIONS
13.5 Total Sulfur. The gas shall not contain more than
five grains of total sulfur per Mcf, of which not more than
two grains shall be mercaptan sulfur.
13.6 Oxygen. The gas shall not at any time have an
oxygen content in excess of ten parts per million by volume,
and the parties shall make every reasonable effort to keep the
gas free of oxygen.
13.7 Temperature. The gas shall be delivered at a
temperature not in excess of 120o Fahrenheit or less than 35o
13.8 Inert Substances. The gas shall not contain inert
substances of more than three percent by volume, of which CO2
may not exceed two percent by volume.
13.9 Water Vapor. The gas shall not contain water vapor
in excess of seven pounds per million cubic feet.
13.10 Shipper's Failure to Meet Specifications. If
any gas tendered for receipt by Southern Trails fails at any
time to conform to any of the specifications of this tariff,
Southern Trails shall have the right, upon notification to
Shipper, to refuse to accept all or any portion of such non-
conforming gas until such time as Shipper demonstrates to
Southern Trails' satisfaction that the gas meets Southern
Trails' quality specifications. Such refusal by Southern
Trails to receive non-conforming gas shall not relieve Shipper
of any of its obligations under this tariff. Southern Trails
may, on a nondiscriminatory basis elect to receive non-
conforming gas in such quantities and for such time periods as
Southern Trails determines will not jeopardize its ability to
meet its obligations to its customers or endanger the safe
operation of its transportation system.
13.11 Quality of Southern Trails' Deliveries. Southern
Trails shall deliver to Shipper or for Shipper's account gas
that is of merchantable quality.
13.12 Commingling. Gas received from Shipper will be
commingled with the gas of other Shippers in the system.
Accordingly, the gas of Shipper shall be subject to such
changes in gross heating value per cubic foot and other
specifications as may result from such commingling.