Questar Southern Trails Pipeline Company
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 10/24/2003, Docket: RP03-612-000, Status: Effective
First Revised Sheet No. 78 First Revised Sheet No. 78 : Effective
Superseding: Original Sheet No. 78
GENERAL TERMS AND CONDITIONS
12.14 Preservation of Records. Southern Trails will retain data as may
be required by appropriate authority.
12.15 Measurement Data Corrections. Measurement data corrections will
be processed within six months of the production month with a three-month
rebuttal period. This standard will not apply in the case of deliberate
omission or misrepresentation or mutual mistake of fact. Parties' other
statutory or contractual rights shall not otherwise be diminished by this
12.16 Cut Off. The cut off for the closing of measurement is five
business days after the business month.
13. QUALITY OF GAS
13.1 Heat Content. The gas delivered at each of the points of receipt
and delivery shall contain a gross heating value of not less than 980 Btu's
per cubic foot nor more than 1,150 Btu's per cubic foot.
13.2 Merchantability. The gas shall be commercially free from dust,
gums, gum-forming constituents, dirt, impurities or other solid or liquid
matter which might interfere with its merchantability or cause injury to or
interference with proper operation of the pipelines, regulators, meters, or
other equipment of Southern Trails. The gas shall also be free of all matter
that is deemed hazardous or toxic and is subject to regulation by the
Environmental Protection Agency or any State agency having similar
jurisdiction or authority.
13.3 Hydrocarbon Dew Point. Shall have a hydrocarbon dew point of no
more than 60 degrees Fahrenheit at 800 psig and/or no more condensable
hydrocarbons in free liquid form than that which constitutes a wetting of the
pipe walls in the lines of the inlet side of any pressure-reducing regulator
in the delivery facilities, or in the absence of such regulator no more such
free hydrocarbon liquids shall be present in the piping at the point of
delivery than that which constitutes a mere dampening of the pipe walls.
13.4 Hydrogen Sulfide. The gas shall not contain more than .25 grain
of H2S per 100 cubic feet.