Tres Palacios Gas Storage LLC
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 08/01/2008, Docket: RP08-424-000, Status: Effective
Original Sheet No. 140 Original Sheet No. 140
GENERAL TERMS AND CONDITIONS
(a) Be commercially free from objectionable odors,
dirt, dust, iron particles, gums, gum-forming constituents,
gasoline, PCBs, and other solid and/or liquid matter, including
but not limited to water, Gas treating chemicals and well
completion fluids and debris, which may become separated from the
Gas during the transportation thereof.
(b) Contain not more than one fourth (1/4) of one grain
of hydrogen sulfide per one hundred (100) cubic feet, as
determined by the cadmium sulfate quantitative test, nor more than
twenty (20) grains of total sulfur per one hundred (100) cubic
(c) The Gas delivered hereunder shall not contain more
than two-tenths of one percent (0.2%) by volume of oxygen, shall
not contain more than three percent (3%) by volume of carbon
dioxide, shall not contain more than three (3%) by volume of
nitrogen, and shall not contain a combined total of carbon dioxide
and nitrogen components of more than four (4%) by volume.
(d) Have a heating value of not less than nine hundred
and sixty-seven (967) Btus per cubic feet and not more than eleven
hundred (1100) Btus per cubic feet.
(e) Have a temperature of not more than 120 degrees
Fahrenheit (120 degrees F), nor less than forty degrees Fahrenheit
(40 degrees F).
(f) Have been dehydrated by the tendering party, by any
method other than the use of a calcium chloride as desiccant, for
removal of entrained water in excess of seven (7) pounds of water
per million (1,000,000) cubic feet of Gas as determined by
dew-point apparatus approved by the Bureau of Mines or such other
apparatus as may be mutually agreed upon.
10.2 Rejection of Gas. Either party shall be entitled
to reject any Gas tendered to it by the other party which does not
meet the minimum specifications of Section 10.1 hereunder.
Acceptance of such Gas does not constitute any waiver of TRES
PALACIOS' right to refuse to accept similarly nonconforming Gas.
11. PRESSURE AND INJECTION/WITHDRAWAL RATES
11.1 Delivery Pressures. TRES PALACIOS shall deliver
Gas to Customer at pressures sufficient to enter the pipeline
facilities at the Point(s) of Delivery against the operating
pressures maintained by Transporter(s) from time to time. TRES
PALACIOS shall not be required to deliver Gas at pressures in
excess of those required by Transporter(s) or in excess of
Transporter(s) maximum allowable operating pressure (MAOP).
Customer shall deliver or cause to be delivered to TRES PALACIOS
all Gas for wheeling, parking or injection at the Point(s) of
Receipt at pressures not less than 700 psig and not in excess of
the MAOP of TRES PALACIOS' facilities at the Point(s) of Receipt.
TRES PALACIOS shall be responsible for maintaining facilities at
such Point(s) of Receipt to permit Customer to deliver Gas to TRES
PALACIOS at such allowed pressures.