Venice Gathering System, L. L. C.
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 01/01/1998, Docket: CP97-533-002, Status: Effective
Original Sheet No. 154 Original Sheet No. 154 : Effective
GENERAL TERMS AND CONDITIONS
15. GAS QUALITY
Unless otherwise specified in an executed Service
Agreement, all gas received by VGS from Customer shall
conform to the following quality specifications:
a. Heating Value. The gas shall have a
heating value of not less than one
thousand twenty Btus per standard cubic
foot (1020 Btus/Scf), unless the contract
was dated prior to August 19, 1997, in
which case the heating value shall not
be less than nine hundred seventy Btus
per standard cubic foot (970 Btus/Scf).
b. Water Vapor. The gas shall not contain
c. Inerts and Oxygen. The gas shall not
contain more than four percent (4%) by
volume of total inerts or two-tenths of
one percent (0.2%) by volume of oxygen.
d. Carbon Dioxide and Nitrogen. The gas
shall not contain more than three percent
(3%) by volume of carbon dioxide or two
percent (2%) by volume of nitrogen.
e. Hydrogen Sulfide. The gas shall not
contain more than one-quarter grain of
hydrogen sulfide per one hundred standard
cubic feet (1/4 gr/100 Scf).
f. Mercaptans. The gas shall not contain
more than one-quarter grain of mercaptans
per one hundred standard cubic feet (1/4