Panhandle Eastern Pipe Line Company, LP
THIRD REVISED VOLUME NO. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 06/30/2004, Docket: RP04-321-000, Status: Effective
Original Sheet No. 216 Original Sheet No. 216 : Effective
GENERAL TERMS AND CONDITIONS
4.3 All measuring stations shall be acceptable to Panhandle
and Shipper and installed and operated to conform to
recognized industry standards, using flange connections
and, where necessary, pulsation dampening equipment.
Auxiliary equipment shall be installed so as not to
interfere with the measurement of either party.
4.4 Either Panhandle or Shipper may witness the installation
or maintenance of the other's equipment. Neither
Panhandle nor Shipper shall be required to verify accuracy
more often than once during any 30 Day period. If, upon
test, accuracy is found to be within 2% by volume
(chromatograph/calorimeter within 0.5%), measurements
taken by such equipment shall be assumed to have been
accurate. Any error exceeding these percentages shall
require correction to zero error of previous recordings
back to the date error began. If the beginning date of
error is unknown, correction shall extend to one-half the
time since the last test, not to exceed 16 Days.
4.5 Where wellhead compressors have been installed, the
maximum permissible Square Root Error Indicator (SREI)
shall be no greater than 1% for volumes less than 2 MMcf
per Day and .5% for volumes greater than 2 MMcf per Day.
The SREI shall be determined by tests at the orifice taps
and shall be performed on the full operating range of the