Kern River Gas Transmission Company
Second Revised Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 07/01/2000, Docket: RP00-288-000, Status: Effective
Original Sheet No. 724 Original Sheet No. 724 : Effective
RATE SCHEDULE MO-1
Kern River Firm Transportation Services
ARTICLE V - QUALITY OF GAS (Continued)
5.3 Gas Blending Rights. (Continued)
(f) Six percent (6.0%) by volume of inerts, subject to the condition
that the volume weighted average total inerts of the Composite Gas
Stream shall not exceed four percent (4.0%).
5.4 Quality Tests.
(a) Location of Tests. The quality of the Gas received and delivered
by Transporter hereunder shall be determined by tests which
Transporter shall cause to be made at each Receipt and Delivery
Point and other locations along its system.
(b) Specification for Tests. Transporter shall determine the Total
Heating Value of Gas and its component analysis at least once each
Month in accordance with the Gas Measurement Committee Report No.
3 prepared by the Gas Measurement Committee of the American Gas
Association, dated September 1985 or any subsequent revisions (AGA-
3). Such determination shall be made using either an on-line
chromatograph or by chromatographic analysis of a representative
sample of Gas taken with a continuous flow proportional sampler.
Chromatography shall be performed in accordance with Gas
Processors Association (GPA) publications 2261-86 and 2286-86 or
any subsequent revisions. The values of the physical constants
for the Gas components shall be determined by the use of the
physical constants listed in Table 5 of AGA-3. For components of
the Gas not listed in said Table 5, GPA publication 2145-88 or any
subsequent revision shall be used.