Egan Hub Storage, LLC
First Revised Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 02/01/2009, Docket: RP09-160-000, Status: Effective
Second Revised Sheet No. 141 Second Revised Sheet No. 141
Superseding: First Revised Sheet No. 141
GENERAL TERMS AND CONDITIONS
(a) Be commercially free from objectionable odors, dirt, dust, iron particles,
gums, gum-forming constituents, gasoline, PCB's, and other solid and/or liquid matter,
including but not limited to water, Gas treating chemicals and well completion fluids and
debris, which may become separated from the Gas during the transportation thereof.
(b) Contain not more than one fourth (1/4) of one grain of hydrogen sulphide
per one hundred (100) Cubic Feet of Gas, as determined by the cadmium sulfate quantitative
test, nor more than twenty (20) grains of total sulphur per one hundred (100) Cubic Feet of
(c) The Gas delivered hereunder shall not contain more than two-tenths of one
percent (0.2%) by volume of oxygen, shall not contain more than three percent (3%) by volume of
carbon dioxide, shall not contain more than three (3%) by volume of nitrogen, and shall not
contain a combined total of carbon dioxide and nitrogen components of more than four (4%) by
(d) Have a heating value of not less than nine hundred and sixty-seven (967)
Btu's per Cubic Feet of Gas and not more than eleven hundred (1100) Btu's per Cubic Feet of
(e) Have a temperature of not more than one hundred twenty degrees Fahrenheit
(120 degrees F), nor less than forty degrees Fahrenheit (40 degrees F).
(f) Have been dehydrated by the tendering party, by any method other than the
use of a calcium chloride as desiccant, for removal of entrained water in excess of seven (7)
pounds of water per million (1,000,000) Cubic Feet of Gas as determined by dew-point apparatus
approved by the Bureau of Mines or such other apparatus as may be mutually agreed upon.
10.2 Rejection of Gas. Either party shall be entitled to reject any Gas tendered to
it by the other party which does not meet the minimum specifications of Section 10.1 hereunder.
Acceptance of such Gas does not constitute any waiver of Egan Hub's right to refuse to accept
similarly nonconforming Gas.
11. PRESSURE AND INJECTION/WITHDRAWAL RATES
11.1 Delivery Pressures. Egan Hub shall deliver Gas to Customer at pressures
sufficient to enter the pipeline facilities at the Point(s) of Delivery located on Egan Hub's
system against the operating pressures maintained by the interconnected pipeline(s). Egan Hub
shall not be required to deliver Gas at pressures in excess of those required by the
interconnected pipeline(s) or in excess of the maximum allowable operating pressure (MAOP) of
the interconnected pipeline(s), not to exceed 1,000 Psig. Customer shall deliver or cause to
be delivered to Egan Hub all Gas for wheeling, parking or injection at the Point(s) of Receipt
located on Egan Hub's system at pressures not less than 800 psig and not in excess of the MAOP
of Egan Hub's facilities at the Point(s) of Receipt. Egan Hub shall be responsible for
maintaining facilities at such Point(s) of Receipt to permit Customer to deliver Gas to Egan
Hub at such allowed pressures.