Arlington Storage Company, LLC
First Revised Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 11/08/2009, Docket: RP10-67-000, Status: Effective
Original Sheet No. 140 Original Sheet No. 140
GENERAL TERMS AND CONDITIONS
(a) Be commercially free from objectionable odors, dirt, dust, iron particles, gums,
gum-forming constituents, gasoline, PCBs, and other solid and/or liquid matter,
including but not limited to water, Gas treating chemicals and well completion
fluids and debris, which may become separated from the Gas during the transportation
(b) Contain not more than one fourth (1/4) of one grain of hydrogen sulfide per one hundred
(100) cubic feet, as determined by the cadmium sulfate quantitative test, nor more than
twenty (20) grains of total sulfur per one hundred (100) cubic feet.
(c) The Gas delivered hereunder shall not contain more than two-tenths of one percent (0.2%)
by volume of oxygen, shall not contain more than three percent (3%) by volume of carbon
dioxide, shall not contain more than three (3%) by volume of nitrogen, and shall not
contain a combined total of carbon dioxide and nitrogen components of more than four
(4%) by volume.
(d) Have a heating value of not less than nine hundred and sixty-seven (967) Btus per
cubic feet and not more than eleven hundred (1100) Btus per cubic feet.
(e) Have a temperature of not more than 120 degrees Fahrenheit (120 degrees F), nor less than
forty degrees Fahrenheit (40 degrees F).
(f) Have been dehydrated by the tendering party, by any method other than the use of a calcium
chloride as desiccant, for removal of entrained water in excess of seven (7) pounds of water
per million (1,000,000) cubic feet of Gas, at a pressure base of fourteen and seventy three
hundredths (14.73) pounds per square inch and a temperature of sixty degrees Fahrenheit
(60 degrees F), as determined by dew-point apparatus approved by the Bureau of Mines or
such other apparatus as may be mutually agreed upon.
10.2 Rejection of Gas. Either party shall be entitled to reject any Gas tendered to it by the
other party which does not meet the minimum specifications of Section 10.1 hereunder.
Acceptance of such Gas does not constitute any waiver of ASC's right to refuse to accept
similarly nonconforming Gas.
11. PRESSURE AND INJECTION/WITHDRAWAL RATES
11.1 Delivery Pressures. ASC shall deliver Gas to Customer at pressures sufficient to enter the
pipeline facilities at the Point(s) of Delivery against the operating pressures maintained
by Transporter(s) from time to time. ASC shall not be required to deliver Gas at pressures
in excess of those required by Transporter(s) or in excess of Transporter(s) maximum allowable
operating pressure (MAOP). Customer shall deliver or cause to be delivered to ASC all Gas
for wheeling, parking or injection at the Point(s) of Receipt at pressures not less than
650 psig and not in excess of the MAOP of ASC's facilities at the Point(s) of Receipt.
ASC shall be responsible for maintaining facilities at such Point(s) of Receipt to permit
Customer to deliver Gas to ASC at such allowed pressures.