Southern LNG Inc.
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 03/01/2010, Docket: RP10-271-000, Status: Effective
First Revised Sheet No. 43 First Revised Sheet No. 43
Superseding: Original Sheet No. 43
GENERAL TERMS AND CONDITIONS
3.3 All LNG loaded in Customer's vessel(s) shall conform to the specifications set forth in this
section, and Customer agrees to analyze or caused to be analyzed each cargo of LNG as provided
in this section. Customer agrees to test each LNG cargo in the manner prescribed.
(a) Hydrogen Sulfide:
The LNG received by Southern LNG shall contain not more than the specified volume of
hydrogen sulfide as determined by methods presented in Standards for Gas Service,
Circular of the National Bureau of Standards, No. 405, page 134 (1934 edition), and
shall be considered free from hydrogen sulfide if a strip of white filter paper,
moistened with a solution containing five per cent (5%) by weight of lead acetate, is
not distinctly darker than a second paper freshly moistened with the same solution
after the first paper has been exposed to the vaporized LNG for one (1) minute in an
apparatus of approved form, through which the vaporized LNG is flowing at the rate of
approximately five (5) standard cubic feet per hour, the vaporized LNG not impinging
directly from a jet upon the test paper.
(b) Total Sulfur:
The LNG received by Southern LNG shall contain not more than the specified total
sulfur as determined by the method prescribed in American Society for Testing and
Materials, Standard Method of Test for Total Sulphur in Fuel Gases, No. D 1072-56.
3.4 Should any LNG for receipt by Southern LNG fail at any time to conform to any of the
specifications provided for in this Section 3, Southern LNG may, at its option, suspend all or
a portion of the receipt of any such LNG. Southern LNG shall be relieved of any of its
obligations for the duration of such suspension. Upon receipt of Southern LNG's notice of such
a failure, Customer shall make a diligent effort to correct the failure by treatment or
dehydration consistent with prudent operation so as to tender LNG conforming to the
specifications provided for in this Section 3.