Saltville Gas Storage Company L.L.C.
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 02/07/2008, Docket: RP08-156-000, Status: Effective
First Revised Sheet No. 140 First Revised Sheet No. 140 : Effective
Superseding: Original Sheet No. 140
GENERAL TERMS AND CONDITIONS
10.1 Specifications. Unless Saltville waives the specification
detailed herein, the Gas received or delivered hereunder shall
meet the quality specifications of each Transporter which receives
or delivers such Gas to Saltville, at any Point of Receipt or
Point of Delivery, and shall in all events be of such quality that
it shall meet at least the following specifications:
(a) Be commercially free of objectionable odors, dirt, dust,
iron particles, gums, gum-forming constituents, gasoline,
PCBs, and other solid and/or liquid matter, including but
not limited to water, gas treating chemicals and well
completion fluids and debris, which may become separated
from the Gas during transportation thereof.
(b) Contain not more than one fourth (1/4) of one grain of
hydrogen sulfide per one hundred (100) cubic feet, as
determined by the cadmium sulfate quantitative test, nor
more than twenty (20) grains of total sulfur per one hundred
(100) cubic feet.
(c) The Gas delivered hereunder shall not contain more than
0.05% by volume of oxygen, shall not contain more than two
percent (2%) by volume of carbon dioxide, shall not contain
more than two percent (2%) by volume of nitrogen, and shall
not contain a combined total of carbon dioxide and nitrogen
components of more than four percent (4%) by volume.
(d) Have a heating value of not less than nine hundred and
sixty-seven (967) BTUs per cubic feet and not more than one
thousand and sixty (1060) BTUs per cubic feet.
(e) Have a temperature of not more than one hundred twenty
degrees Fahrenheit (120°F), nor less than forty degrees
(f) Have been dehydrated by the tendering party, by methods
generally acceptable to the industry (excluding the use of a
calcium chloride as desiccant), for removal of entrained
water in excess of seven (7) pounds of water per million
(1,000,000) cubic feet of Gas.
10.2 Rejection of Gas. Saltville shall be entitled to reject any Gas
tendered to it hereunder which does not meet the minimum
specifications of Section 10.1. Acceptance at any time of Gas
which does not meet these quality standards does not constitute
any waiver of Saltville's right to refuse to accept similarity