Sabine Pipe Line Company LLC
Second Revised Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 07/31/1993, Docket: RS92- 78-003, Status: Effective
Original Sheet No. 275 Original Sheet No. 275 : Superseded
12. GAS QUALITY
All gas received by Sabine from Shipper shall conform
to the following quality specifications:
a) Heating Value. The gas shall have a heating value
of not less than nine hundred seventy Btus per
standard cubic foot (970 Btus/Scf).
b) Water Vapor. The gas shall not contain more than
seven pounds of water per million standard cubic
feet (7 lbs/MMcf).
c) Oxygen. The gas shall not contain more than two-
tenths of one percent (0.2%) by volume of oxygen.
d) Carbon Dioxide and Nitrogen. The gas shall not
contain more than three percent (3%) by volume of
a combined total of carbon dioxide and nitrogen.
e) Hydrogen Sulfide. The gas shall not contain more
than one-quarter grain of hydrogen sulfide per one
hundred standard cubic feet (1/4 gr/100 Scf).
f) Mercaptans. The gas shall not contain more than
one-quarter grain of mercaptans per one hundred
standard cubic feet (1/4 gr/100 Scf).
g) Total Sulfur. The gas shall not contain more than
five grains of total sulfur per one hundred
standard cubic feet (5 grs/100 Scf).
h) Dust, Gums and Solid Matter. The gas shall be
commercially free from dust, gums, gum-forming
constituents, and other solid matter.
i) Liquid Hydrocarbons. The gas shall be free of
hydrocarbons in liquid form at the temperature and
pressure at which the gas is received.