Southeast Supply Header, LLC
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 09/04/2008, Docket: CP07-44-005, Status: Effective
Original Sheet No. 221 Original Sheet No. 221
GENERAL TERMS AND CONDITIONS
3. QUALITY OF GAS (continued)
(h) The flowing Gas shall not have a temperature of more than
one-hundred twenty degrees (120) Fahrenheit or less than
forty (40) degrees Fahrenheit.
(i) The Gas shall be free of water and hydrocarbons in liquid
form at the temperature and pressure at which the Gas is
received and delivered.
(j) The Gas shall not contain in excess of seven (7) pounds of
water vapor per million cubic feet;
(k) The Gas shall not contain, either in the Gas or in any
liquids with the Gas, any microbiological organism, active
bacteria or bacterial agent capable of contributing to or
causing corrosion and/or operational and/or other problems.
Microbiological organisms, bacteria or bacterial agents
include, but are not limited to, sulfate reducing bacteria
(SRB) and acid producing bacteria (APB). Tests for bacteria
or bacterial agents shall be conducted on samples taken from
the meter run or the appurtenant piping using American
Petroleum Institute (API) test method API-RP38 or any other
test method acceptable to Transporter and Shipper which is
currently available or may become available at any time.
3.2 The test equipment and methodology utilized by Transporter to
determine whether Gas meets the qualify specifications set forth
in Section 3.1 shall be posted on its LINK® System.
3.3 At Transporter's request, Shipper shall use all reasonable efforts
to obtain and provide to Transporter all records regarding Gas
quality kept by upstream pipelines transporting the Gas received
by Transporter for Shipper's account. Shipper shall use all
reasonable efforts to ensure and verify for Transporter that such
upstream pipelines are using appropriate equipment to monitor
compliance with the Gas quality specifications applicable on
Transporter's system as stated in this Section 3.