Liberty Gas Storage, LLC
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 04/15/2007, Docket: RP07-357-000, Status: Effective
Original Sheet No. 134 Original Sheet No. 134 : Effective
GENERAL TERMS AND CONDITIONS
(a) Be commercially free from objectionable odors, dirt, dust, iron
particles, gums, gum-forming constituents, gasoline, PCBs, and other solid
and/or liquid matter, including but not limited to water, Gas treating
chemicals and well completion fluids and debris, which may become separated
from the Gas during the transportation thereof.
(b) Contain not more than one fourth (1/4) of one grain of hydrogen sulfide per
hundred (100) cubic feet, as determined by the cadmium sulfate quantitative
test, nor more than twenty
(20) grains of total sulfur per one hundred (100) cubic feet.
(c) The Gas delivered hereunder shall not contain more than two-tenths of
(0.2%) by volume of oxygen, shall not contain more than three percent (3%) by
volume of carbon dioxide, shall not contain more than three (3%) by volume of
nitrogen, and shall not contain a combined total of carbon dioxide and nitrogen
components of more than four (4%) by volume.
(d) Have a heating value of not less than nine hundred and sixty-seven
(967) Btus per cubic feet and not more than eleven hundred (1100) Btus per
(e) Have a temperature of not more than 120 degrees Fahrenheit (120 degrees
F), nor less than forty degrees Fahrenheit (40 degrees F).
(f) Have been dehydrated by the tendering party, by any method other than
the use of a calcium chloride as desiccant, for removal of entrained water in
excess of seven (7) pounds of water per million (1,000,000) cubic feet of Gas
as determined by dew-point apparatus approved by the Bureau of Mines or such
other apparatus as may be mutually agreed upon.
10.2 Rejection of Gas. Either party shall be entitled to reject any Gas
tendered to it by the other party which does not meet the minimum
specifications of Section 10.1 hereunder. Acceptance of such Gas does not
constitute any waiver of Liberty's right to refuse to accept similarly
11. PRESSURE AND INJECTION/WITHDRAWAL RATES
11.1 Delivery Pressures. Liberty shall deliver Gas to Customer at pressures
sufficient to enter the pipeline facilities at the Point(s) of Delivery located
on Liberty's system against the operating pressures maintained by
Transporter(s) from time to time. Liberty shall not be required to deliver Gas
at pressures in excess of those required by Transporter(s) or in excess of
Transporter(s) maximum allowable operating pressure (MAOP), not to exceed 1,300
psig. Customer shall deliver or cause to be delivered to Liberty all Gas for
wheeling, parking or injection at the Point(s) of Receipt located on Liberty's
system at pressures not less than 800 psig and not in excess of the MAOP of
Liberty's facilities at the Point(s) of Receipt. Liberty shall be responsible
for maintaining facilities at such Point(s) of Receipt to permit Customer to
deliver Gas to Liberty at such allowed pressures.