Garden Banks Gas Pipeline, LLC
Original Volume No. 1
Contents / Previous / Next / Main Tariff Index
Effective Date: 05/10/2010, Docket: RP10-594-000, Status: Effective
First Revised Sheet No. 63 First Revised Sheet No. 63
Superseding: Original Sheet No. 63
GENERAL TERMS AND CONDITIONS
The quality specifications herein shall apply to all gas delivered to
Transporter by Shipper under Rate Schedules FT-1, FT-2 and IT-1.
All gas delivered or caused to be delivered by Shipper to
Transporter at the Receipt Point(s) shall conform to the following
quality specifications, or any more stringent quality
specifications of a downstream pipeline, any of which may be
waived by Transporter in its discretion on a nondiscriminatory
(a) Oxygen. The gas shall not contain more than two-tenths of
one percent (0.2%) by volume of oxygen, and Shipper shall
make every reasonable effort to keep the gas free of oxygen.
(b) Liquids. The gas shall contain no more than 7 pounds of
water vapor per million cubic feet.
(c) Hydrogen Sulfide. The gas shall not contain more than 0.25
of a grain of hydrogen sulfide per hundred cubic feet.
(d) Temperature. The gas shall have a temperature of not more
than one hundred twenty degrees (120) Fahrenheit and not
less than forty (40) degrees Fahrenheit.
(e) Sulfur. The gas shall not contain more than twenty (20)
grains of total sulfur per hundred cubic feet.
(f) Carbon Dioxide/Nitrogen. The gas shall not contain more
than three percent (3%) by volume of a combined total of
carbon dioxide and nitrogen components; provided, however,
that the total carbon dioxide content shall not exceed two
percent (2%) by volume.